UPS and generator can deliver innovative critical power solutions to provide businesses with uninterruptible power and backup power supplies.
A UPS can support its critical load during utility power anomalies and blackouts – but only until its battery autonomy expires. Conversely, an adequately-fuelled generator can support the load indefinitely, but needs time to start up and stabilise.
Operators of any data centres with mission-critical loads must ensure uninterrupted power under all circumstances as most critical power solutions. However, while the electricity network is built to withstand the intense storms that can affect any part of the country at any time, extreme weather can affect overhead power lines. Accordingly, although the organisation has emergency plans and engineers ready to deal with situations as they arise, data centres should also have their own plans in place.
Such plans must include provision for power cuts lasting several hours or possibly days, as well as those of just seconds’ or minutes’ duration. This in turn calls for an on-site generator to back up the UPS, as all UPS battery autonomies are finite, and susceptible to be exceeded by a sufficiently extended blackout. Additionally, there is no point in having battery autonomy that is not matched by air conditioning that can maintain safe operating temperatures for the UPS throughout the blackout.
The UPS is the front line
If a data centre is regarded as mission-critical, it will almost certainly have an online UPS. During normal, ‘mains OK’ operation, the incoming power flows through the UPS rectifier and inverter components before reaching the load. This means that the load is continuously protected from mains-borne noise, surges, spikes, brownouts and any other aberrations, as well as short term power cuts safely within the UPS battery autonomy. Under these circumstances, the UPS is providing full protection without support from the generator, which remains on standby.
However, if the UPS control system detects that an ongoing blackout is becoming a threat to its battery autonomy, it could signal the critical load, allowing it to shut down gracefully within the remaining autonomy. Alternatively, if losing the data processing resource is not an option, the UPS must start interacting with an on-site generator. The UPS’s role is then to maintain the supply until the generator can start, stabilise and take over seamlessly as the power source. Assuming the generator has been correctly sized for the application, the UPS will accept it as a ‘mains replacement’ for recharging its battery and supplying the critical load until mains power is restored. This period can be indefinite, subject only to continued availability of fuel for the generator.
The generator as a standby power source
To correctly specify an optimally-matched UPS/generator power protection pair, it’s necessary to look more closely at the generator characteristics and requirements.
The generator converts stored energy – fuel – into electrical energy. It comprises the fuel itself, an engine to develop mechanical energy, and an alternator to convert the mechanical energy into electrical form.
The engine must be well maintained with an adequate fuel supply at all times. The battery must be healthy enough to assure reliable starting on demand, while coolant and oil levels should be regularly checked.
The engine drives an alternator, which converts mechanical power into an alternating supply of typically either 220V/230V single-phase or 380V/400V three-phase. This output voltage’s amplitude and stability is controlled by an Automatic Voltage Regulator (AVR) while the frequency – usually 50 Hz or 60 Hz – is determined by the engine speed. Engine speed and supply frequency are set by a governor, which regulates the fuel supply to the engine; more fuel increases speed and frequency.
Both mechanical and electronic governors are available. Mechanical governors, although lower-cost than electronic types, are less responsive and provide less stable engine speed and voltage frequency regulation. An electronic governor counts teeth on the alternator’s flywheel as it rotates, and regulates the fuel flow accordingly. Electronic governing is highly responsive and offers very stable speed and frequency regulation; accordingly, it is usually specified for any standby generator intended for pairing with a UPS system.
A UPS standby generator should have a mains-powered engine water heater and battery charger. It must also communicate when it starts and stops in response to mains supply failure and subsequent restoration. This is usually handled by an Automatic Mains Failure (AMF) panel that includes the necessary signals.
To avoid the AMF starting the generator for every short supply aberration, it is usually set to operate only if the mains fails for an extended time of typically two to 10 seconds. Similarly, the AMF should not stop the generator and switch the UPS back to mains supply immediately it is restored; the reconnection may be part of the utility company’s fault location procedure or the result of an automatic breaker operation. The fault may still exist, causing the supply to be disconnected again almost immediately. Accordingly, most AMF-controlled generators are set to continue to supply power for at least two minutes after the utility supply is restored.
To ensure the generator performs reliably as a power protection component, it must be correctly sized as well as matched to the UPS. In fact, it should be oversized, especially as it usually supports more equipment than the UPS; air conditioning to cool the equipment as well as emergency lighting, communications and alarm systems.
Critical power solutions summary
If a data centre is providing a critical ICT resource that has to remain online under all circumstances, then an on-site generator must be provided to back up the UPS if a long-duration blackout occurs. Additionally, for successful operation as part of the power protection strategy critical power solutions, the generator must be carefully matched to the UPS characteristics and sized sufficiently to handle all the emergency power needed during a blackout.
|Prostar PHR1110 true double conversion rack mounted online ups 10 kva||Prostar PHR1106 uninterruptible power supply rack mountable ups 6 kva||Prostar PHR1103 19 inch server compact rack mounting online ups 3 kva|
- How does an uninterruptible power supply work?
- You should know the ups technical glossary
- Lithium-ion battery – Wikipedia
- Five most effective ways to maximise your UPS energy efficiency
- Why Do I Need a UPS?
- The benefits of lithium-ion batteries in data centre ups systems
- Why only online UPS topology provides mission critical load protection